The manual call point has been designed to operate on a loop of intelligent fire
detection devices .When activated; it interrupts the polling cycle for a very fast
response. The M-MCP-ID manual call point with inbuilt isolator is intended for indoor
applications. The address of each call point is set at the commissioning stage by
means of a seven-segment DIL switch. The address switch isaccessible without removing
the call point from the mounting surface.A red alarm LED is provided on the call
point. This LED is controlled independent of the call point, by the control panel.
Once activated, the manual call point can be reset by inserting the reset key into
the front facing LED, turning clockwise until a reset occurs.